annual cost savings
annual electric savings
annual gas savings
utility incentives identified
retro-commissioning on campus
Any skepticism dissolved instantly among Microsoft Silicon Valley campus site staff after seeing project results first hand with staff stating:
This is a good project, we should have done it 5 years ago.
We performed retro-commissioning at Microsoft’s high tech campus in Silicon Valley under PG&E’s “Core” Retro-commissioning (RCx) program.
One of the key measures we identified was limiting the off-hours use of air handlers. While critical areas need to be conditioned, we greatly reduced the equipment required for conditioning needs.
With the site staff’s help, we reduced the nighttime loads dramatically.
energy efficiency measures
- Fume hood standby airflow reduction
- Scheduled half of air handlers off overnight, even with 24-7 lab loads
- Trim and respond controls sequences on all air handlers (Supply air temperature and discharge pressure)
- Improved chiller water controls
identified energy savings
750,000 kWh (verified savings exceeded this)
Additional energy saving measures included supply air temperature and discharge pressure controls.
Our team used trim and respond sequences adapted from ASHRAE’s Research Project 1455 to optimize temperature and pressure response minimizing energy use while maintaining critical, tight set-point zone control.